Frequently Asked Question
To properly measure the voltage of a UPS without pure sine wave output, you need a special meter with true RMS. UPSs with Pulse Width Modulated output (square wave) will show proper 230VAC in the software, but measured voltage might be lower (i.e. ~160VAC). This value is expected if basic multimeter is used.